// CODE SNIPPET
401.6 Contaminant Sources
JUMP TO FULL CODE CHAPTER
Stationary local sources producing air-borne particulates, heat, odors, fumes, spray, vapors, smoke or gases in such quantities as to be irritating or injurious to health shall be provided with an exhaust system in accordance with Chapter 5 or a means of collection and removal of the contaminants. Such exhaust shall discharge directly to an approved location at the exterior of the building.
Related Code Sections
401.6 Ventilation, Contaminant Sources
Stationary local sources producing air-borne particulates, heat, odors, fumes, spray, vapors, smoke or gases in such quantities as to be irritating ...
1203.5.2 Interior Environment, Contaminants Exhausted
Contaminant sources in naturally ventilated spaces shall be removed in accordance with the International Mechanical Code and the International ...
2015 Michigan Building Code > 12 Interior Environment > 1203 Ventilation > 1203.5 Natural Ventilation > 1203.5.2 Contaminants Exhausted
R303.5.1 Building Planning, Intake Openings
-foot (3048 mm) separation is not required where the intake opening is located 3 feet (914 mm) or greater below the contaminant source. Vents ...
2015 Michigan Residential Code > 3 Building Planning > R303 Light, Ventilation and Heating > R303.5 Opening Location > R303.5.1 Intake Openings
606.5.8 Water Supply and Distribution, Prohibited Location of Potable Supply Tanks
Potable water gravity tanks or manholes of potable water pressure tanks shall not be located directly under any soil or waste piping or any source ...
2015 Michigan Plumbing Code > 6 Water Supply and Distribution > 606 Installation of the Building Water Distribution System > 606.5 Water Pressure Booster Systems > 606.5.8 Prohibited Location of Potable Supply Tanks
P2902.1 Water Supply and Distribution, General
a cross-connection between the supply and a source of contamination except where approved backflow prevention assemblies, backflow prevention devices ...
2015 Michigan Residential Code > 29 Water Supply and Distribution > P2902 Protection of Potable Water Supply > P2902.1 General