// CODE SNIPPET
2184.108.40.206.2 Container Stability
JUMP TO FULL CODE CHAPTER
A method of rigidly supporting the container during the venting of CNG shall be provided. The selected method shall provide not less than two points of support and shall prevent the horizontal and lateral movement of the container. The system shall be designed to prevent the movement of the container based on the highest gas-release velocity through valve orifices at the container's rated pressure and volume. The structure or appurtenance shall be constructed of noncombustible materials.
Related Code Sections
Article 12 Foundations, Stability
Stability against overturning shall be provided by the dead load of the building, by the allowable uplift capacity of piling, by anchors ...
1605.1.1 Structural Design, Stability
Regardless of which load combinations are used to design for strength, where overall structure stability (such as stability against overturning ...
NYC Building Code 2014 > 16 Structural Design > 1605 Load Combinations > 1605.1 General > 1605.1.1 Stability
1808.2.5 Soils and Foundations, Stability
Piers or piles shall be braced to provide lateral stability in all directions. Three or more piles connected by a rigid cap shall be considered ...
NYC Building Code 2008 > 18 Soils and Foundations > 1808 Pier and Pile Foundations > 1808.2 Piers and Piles—General Requirements > 1808.2.5 Stability
803.2 Interior Finishes, Stability
Interior finish materials regulated by this chapter shall be applied or otherwise fastened in such a manner that such materials will not readily ...