// CODE SNIPPET
69.2.2 Container Appurtenances and Regulators
Related Code Sections
69.2.2 Liquefied Petroleum Gases and Liquefied Natural Gases, Container Appurtenances and Regulators
Container appurtenances and regulators shall be fabricated of materials that are compatible with LP-Gas, shall be resistant to the action of LP-Gas ...
Fire Code 2015 of Delaware > 69 Liquefied Petroleum Gases and Liquefied Natural Gases > 69.2 LP-gas Equipment and Appliances > 69.2.2 Container Appurtenances and Regulators
69.3.1* Liquefied Petroleum Gases and Liquefied Natural Gases, Application
Installation of container appurtenances and regulators Installation of piping (including flexible connectors and hose), hydrostatic relief valves ...
Fire Code 2015 of Delaware > 69 Liquefied Petroleum Gases and Liquefied Natural Gases > 69.3 Installation of LP-gas Systems > 69.3.1* Application
184.108.40.206 Compressed Gases and Cryogenic Fluids, Physical Protection
Containers, piping, valves, pressure relief devices, regulating equipment, and other appurtenances shall be protected against physical damage ...
Fire Code 2015 of Delaware > 63 Compressed Gases and Cryogenic Fluids > 63.4 Cryogenic Fluids > 63.4.6 Security > 220.127.116.11 Physical Protection
18.104.22.168 Definitions, Appurtenance.
An accessory or attachment that enables the private fire service main to perform its intended function. [ 24, 2013 ...
Standard for the Installation of Sprinkler Systems 2013 of Delaware > 3 Definitions > 3.8 Private Water Supply Piping Definitions > 3.8.1 General Definitions From NFPA 24 > 22.214.171.124 Appurtenance.
126.96.36.199.5 Refueling, Tank Appurtenances
Vent pipes that are provided for normal tank venting shall terminate outside the vault and at least 12 ft (3.6 m) above ground level and shall meet ...
Fire Code 2015 of Delaware > 42 Refueling > 42.3 Storage of Liquids > 42.3.3 Storage of Liquids > 188.8.131.52 Vaults for Aboveground Tanks > 184.108.40.206.5 Tank Appurtenances