// CODE SNIPPET
(A) Constant-Voltage Generators
Related Code Sections
(A) Equipment for General Use, Constant-Voltage Generators
Constant-voltage generators, except ac generator exciters, shall be protected from overload by inherent design, circuit breakers, fuses, protective ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 445 Generators > 445.12 Overcurrent Protection > (A) Constant-Voltage Generators
620.3 Special Equipment, Voltage Limitations
and feeders to motor controllers, driving machine motors, machine brakes, and motor-generator sets shall not have a circuit voltage in excess of 1000 ...
National Electrical Code 2020 of Minnesota > 6 Special Equipment > 620 Elevators, Dumbwaiters, Escalators, Moving Walks, Platform Lifts, and Stairway Chairlifts > 620.3 Voltage Limitations
(A) Special Occupancies, Installations
to simultaneously disconnect all power. Such isolation shall be accomplished by means of one or more isolation transformers, by means of generator sets ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 517 Health Care Facilities > 517.160 Isolated Power Systems > (A) Installations
188.8.131.52 Public Emergency Alarm Reporting Systems, Constant-Current (100 Milliampere) Systems
Constant-current systems shall comply with the requirements of 184.108.40.206.1 through 220.127.116.11.6 ...
National Fire Alarm and Signaling Code 2016 of Minnesota > 27 Public Emergency Alarm Reporting Systems > 27.5 Alarm Processing Equipment > 27.5.4 Wired Network Systems > 18.104.22.168 Constant-Current (100 Milliampere) Systems
3106.6.2 Tents, Temporary Special Event Structures and Other Membrane Structures, Generators
Generators shall be installed not less than 10 feet (3048 mm) from combustible materials, and shall be isolated from the public by physical guard ...
2020 Minnesota State Fire Code > 31 Tents, Temporary Special Event Structures and Other Membrane Structures > 3106 Outdoor Assembly Events > 3106.6 Electrical Equipment and Wiring > 3106.6.2 Generators