// CODE SNIPPET
E3705.4.2 Conductors Rated 75°C
Go To Full Code Chapter
Termination provisions of equipment for circuits rated over 100 amperes, or marked for conductors larger than 1 AWG, shall be used only for:
- Conductors rated 75°C (167°F).
- Conductors with higher temperature ratings provided that the ampacity of such conductors does not exceed the 75°C (167°F) ampacity of the conductor size used, or provided that the equipment is listed and identified for use with such conductors. [110.14(C)(1)(b)]
Related Code Sections
E3705.4.2 Branch Circuit and Feeder Requirements, Conductors Rated 75°C
for: Conductors rated 75°C (167°F). Conductors with higher temperature ratings provided that the ampacity of such conductors does not exceed the 75°C (167°F ...
(1) General, Equipment Provisions
and identified for use with such conductors. For motors marked with design letters B, C, or D, conductors having an insulation rating of 75°C (167°F ...
(I) Special Conditions, Limited Power (LP) Cables
cable with 23 AWG conductors, a temperature rating of 75°C, and a current limit of 0.6 amperes per conductor (0.6 A) ...