// CODE SNIPPET
E3705.4.2 Conductors Rated 75°C
JUMP TO FULL CODE CHAPTER
Termination provisions of equipment for circuits rated over 100 amperes, or marked for conductors larger than 1 AWG, shall be used only for:
- Conductors rated 75°C (167°F).
- Conductors with higher temperature ratings provided that the ampacity of such conductors does not exceed the 75°C (167°F) ampacity of the conductor size used, or provided that the equipment is listed and identified for use with such conductors. [110.14(C)(1)(b)]