// CODE SNIPPET
505.18 Conductors and Conductor Insulation
JUMP TO FULL CODE CHAPTER
For type of protection "e," field wiring conductors shall be copper. Every conductor (including spares) that enters Type "e" equipment shall be terminated at a Type "e" terminal.
Related Code Sections
505.18 Special Occupancies, Conductors and Conductor Insulation
vapors or liquids may collect on, or come in contact with, the insulation on conductors, such insulation shall be of a type identified for use under ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 505 Zone 0, 1, and 2 Locations > 505.18 Conductors and Conductor Insulation
(C) Wiring and Protection, Conductor Protection
or dangerous temperatures in conductors or conductor insulation under short-circuit conditions ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 240 Overcurrent Protection > 240.100 Feeders and Branch Circuits > (C) Conductor Protection
399.2 Wiring Methods and Materials, Definition
The definitions in this section shall apply only within this article. Outdoor Overhead Conductors. Single conductors, insulated, covered, or bare ...
National Electrical Code 2020 of Minnesota > 3 Wiring Methods and Materials > 399 Outdoor Overhead Conductors Over 1000 Volts > 399.2 Definition
(B) Special Occupancies, Equipment Grounding Conductors
Bare conductors or conductors with insulation or individual covering that is green or green with one or more yellow stripes shall be used ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 552 Park Trailers > 552.56 Interior Equipment Grounding > (B) Equipment Grounding Conductors
400.22 Equipment for General Use, Grounded-Conductor Identification
A white or gray insulation on one conductor and insulation of a readily distinguishable color or colors on the other conductor or conductors ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 400 Flexible Cords and Flexible Cables > 400.22 Grounded-Conductor Identification