// CODE SNIPPET
Section 1915 Concrete-Filled Steel Columns
JUMP TO FULL CODE CHAPTER
Caps, base plates and connections shall be in accordance with ACI 318 and AISC 360 and shall be positively attached to the shell and anchored to the concrete core. Welding of brackets without mechanical anchorage shall be prohibited. Where the pipe is slotted to accommodate webs of brackets or other connections, the integrity of the shell shall be restored by welding to ensure hooping action of the composite section.
Steel reinforcement shall be in the form of rods, structural shapes or pipe embedded in the concrete core in accordance with ACI 318 and AISC 360 with sufficient clearance to ensure the composite action of the section, but not nearer than 1 inch (25 mm) to the exterior steel shell. Structural shapes used as reinforcement shall be milled to ensure bearing on cap and base plates.
Steel columns shall be of such size or so protected as to develop the required fire-resistance ratings specified in Table 601. Where an outer steel shell is used to enclose the fire protective covering, the shell shall not be included in the calculations for strength of the column section. The minimum diameter of steel columns shall be 4 inches (102 mm) except that in structures of Type V construction not exceeding three stories or 40 feet (12 192 mm) above grade plane, steel columns used in basements and as secondary steel members shall have a minimum diameter of 3 inches (76 mm).
Four minimum 1/2 in. (12.7 mm) diameter holes, top and bottom, shall be placed opposite each other, two at the top and two at the bottom of the column. The two bottom holes shall be rotated 90° relative to the two top holes.
Related Code Sections
Section 1915 Concrete, Concrete-Filled Steel Columns
Concrete-filled steel columns shall comply with Section 1915 and shall be filled with concrete so placed and manipulated as to secure maximum density ...
1915.6 Concrete, Approvals
Details of column connections and splices shall be shop fabricated in accordance with ACI 318 and AISC 360. Concrete-filled steel columns shall ...
1915.5.1 Concrete, Vent Holes
of the column. The two bottom holes shall be rotated 90° relative to the two top holes ...
NYC Building Code 2014 > 19 Concrete > 1915 Concrete-Filled Steel Columns > 1915.5 Fire-Resistance-Rating Protection > 1915.5.1 Vent Holes
1916.1 Concrete, General
Concrete-filled pipe columns shall be manufactured from standard, extra-strong or double-extra-strong steel pipe or tubing that is filled ...
722.214.171.124.1 Fire and Smoke Protection Features, Reentrant Space Filled
For wide-flange steel columns completely encased in concrete with all reentrant spaces filled [Figure 721.5.1(6)(c)], the thermal capacity ...
NYC Building Code 2014 > 7 Fire and Smoke Protection Features > 721 Calculated Fire Resistance > 721.5 Steel Assemblies > 721.5.1 Structural Steel Columns > 7126.96.36.199 Concrete-Protected Columns > 7188.8.131.52.1 Reentrant Space Filled