// CODE SNIPPET
Section 713 Computerized Drainage Design
JUMP TO FULL CODE CHAPTER
The load shall be computed from the simultaneous or sequential discharge conditions from fixtures, appurtenances and appliances or the peak usage design condition.
The discharge profiles for flow rates versus time from fixtures and appliances shall be in accordance with the manufacturer's specifications.
Pipe shall be sized to prevent full-bore flow.
Pipe size calculations shall be conducted with the pipe wall roughness factor (ks), in accordance with the manufacturer's specifications and as modified for aging roughness factors with deposits and corrosion.
Related Code Sections
Section 713 Sanitary Drainage, Computerized Drainage Design
The sizing, design and layout of the drainage system shall be permitted to be designed by approved computer design methods ...
713.3.1 Sanitary Drainage, Selecting Pipe Wall Roughness
Pipe size calculations shall be conducted with the pipe wall roughness factor (ks), in accordance with the manufacturer's specifications ...
Plumbing Code 2018 of Kansas > 7 Sanitary Drainage > 713 Computerized Drainage Design > 713.3 Selections of Drainage Pipe Sizes > 713.3.1 Selecting Pipe Wall Roughness
Section 920 Vents, Computerized Vent Design
The sizing, design and layout of the vent system shall be permitted to be determined by approved computer program design methods ...
920.2 Vents, System Capacity
The vent system shall be based on the air capacity requirements of the drainage system under a peak load condition ...