// CODE SNIPPET
R601.2.1 Compressible Floor-Covering Materials
JUMP TO FULL CODE CHAPTER
Compressible floor-covering materials that compress more than 1/32 inch (0.8 mm) when subjected to 50 pounds (23 kg) applied over 1 inch square (645 mm) of material and are greater than 1/8 inch (3.2 mm) in thickness in the uncompressed state shall not extend beneath walls, partitions or columns, which are fastened to the floor.
Related Code Sections
R601.2.1 Wall Construction, Compressible Floor-Covering Materials
Compressible floor-covering materials that compress more than 1 / 32 inch (0.8 mm) when subjected to 50 pounds (23 kg) applied over 1 inch square ...
Residential Code 2021 of Colorado > 6 Wall Construction > R601 General > R601.2 Requirements > R601.2.1 Compressible Floor-Covering Materials
Section R402 Foundations, Materials
for maximum cementitious materials content. For garage floors with a steel-troweled finish, reduction of the total air content (percent by volume ...
324.41 Wiring Methods and Materials, Floor Coverings
Floor-mounted Type FCC cable, cable connectors, and insulating ends shall be covered with carpet squares not larger than 1.0 m (39.37 in.) square ...
National Electrical Code 2020 of Colorado > 3 Wiring Methods and Materials > 324 Flat Conductor Cable: Type FCC > 324.41 Floor Coverings
390.15 Wiring Methods and Materials, Covering
-type flush raceways with removable covers shall be permitted to be laid flush with the floor surface. Such approved raceways shall be designed so ...
National Electrical Code 2020 of Colorado > 3 Wiring Methods and Materials > 390 Underfloor Raceways > 390.15 Covering