// CODE SNIPPET
504.9 Commercial Clothes Dryers
JUMP TO FULL CODE CHAPTER
The installation of dryer exhaust ducts serving commercial clothes dryers shall comply with the appliance manufacturer's installation instructions. Exhaust fan motors installed in exhaust systems shall be located outside of the airstream. In multiple installations, the fan shall operate continuously or be interlocked to operate when any individual unit is operating. Ducts shall have a minimum clearance of 6 inches (152 mm) to combustible materials. Clothes dryer transition ducts used to connect the appliance to the exhaust duct system shall be limited to single lengths not to exceed 8 feet (2438 mm) in length and shall be listed and labeled for the application. Transition ducts shall not be concealed within construction.
Related Code Sections
504.9 Exhaust Systems, Commercial Clothes Dryers
The installation of dryer exhaust ducts serving commercial clothes dryers shall comply with the appliance manufacturer's installation instructions ...
Mechanical Code 2018 of Maryland > 5 Exhaust Systems > 504 Clothes Dryer Exhaust > 504.9 Commercial Clothes Dryers
Section 913 Specific Appliances, Fireplaces and Solid Fuel-Burning Equipment, Clothes Dryers
in accordance with UL 2158. Electric coin-operated clothes dryers shall be tested in accordance with UL 2158. Electric commercial clothes dryers shall be tested ...
Mechanical Code 2018 of Maryland > 9 Specific Appliances, Fireplaces and Solid Fuel-Burning Equipment > 913 Clothes Dryers
609.1 ENERGY CONSERVATION, EFFICIENCY AND CO2e EMISSION REDUCTION, General
Battery chargers a Automatic ice makers Ceiling fans and ceiling fanlight Commercial clothes washers kits ...
Green Construction Code 2012 of Maryland > 6 ENERGY CONSERVATION, EFFICIENCY AND CO2e EMISSION REDUCTION > 609 Specific Appliances and Equipment > 609.1 General
514.2 Exhaust Systems, Prohibited Applications
systems serving Type I or Type II hoods. Clothes dryer exhaust systems covered in Section 504. Exception: The application of ERV equipment ...
Mechanical Code 2018 of Maryland > 5 Exhaust Systems > 514 Energy Recovery Ventilation Systems > 514.2 Prohibited Applications
126.96.36.199 Building Services, Clothes Dryers
Clothes dryers shall be cleaned to maintain the lint trap and keep the mechanical and heating components free from excessive accumulations of lint ...
State of Maryland Fire Prevention Code > 11 Building Services > 11.5 Heating Appliances > 11.5.1 General > 188.8.131.52 Clothes Dryers