// CODE SNIPPET
918.5 Combustible Material Adjacent to Cooking Top
JUMP TO FULL CODE CHAPTER
Listed and unlisted food service ranges shall be installed to provide clearance to combustible material of not less than 18 inches (457 mm) horizontally for a distance of up to 2 feet (610 mm) above the surface of the cooking top where the combustible material is not completely shielded by high shelving, warming closet, or other system. Reduced combustible material clearances are permitted where protected in accordance with Table 303.10.1. [NFPA 54:10.12.5]
Related Code Sections
918.5 Installation of Specific Appliances, Combustible Material Adjacent to Cooking Top
) horizontally for a distance of up to 2 feet (610 mm) above the surface of the cooking top where the combustible material is not completely shielded by high ...
2018 Uniform Mechanical Code of Nevada > 9 Installation of Specific Appliances > 918.0 Food Service Appliance, Floor Mounted > 918.5 Combustible Material Adjacent to Cooking Top
920.4 Installation of Specific Appliances, Built-In Units
Unlisted built-in household cooking appliances shall not be installed in or adjacent to combustible material ...
2018 Uniform Mechanical Code of Nevada > 9 Installation of Specific Appliances > 920.0 Household Cooking Appliances > 920.4 Built-In Units
M1503.2.1 Exhaust Systems, Open-Top Broiler Exhaust
and cabinets. A clearance of not less than 24 inches (610 mm) shall be maintained between the cooking surface and combustible material and cabinets. The ...
Residential Code 2018 of Nevada > 15 Exhaust Systems > M1503 Domestic Cooking Exhaust Equipment > M1503.2 Domestic Cooking Exhaust > M1503.2.1 Open-Top Broiler Exhaust
Section G2447 Fuel Gas, (623) Cooking Appliances
of the following is installed: The underside of the combustible material or metal cabinet above the cooking top is protected with not less than 1 / 4 inch ...