// CODE SNIPPET
303.2 Closet or Alcove Installations
JUMP TO FULL CODE CHAPTER
Central heating furnaces and boilers installed in closets or alcoves shall be listed for such installation. Central heating furnaces not listed for closet or alcove installation shall be installed in a room or space having a volume not less than 12 times the total volume of the furnace. Central heating boilers not listed for closet or alcove installation shall be installed in a room or space having a volume 16 times the volume of the boiler. Where the ceiling height of the room or space exceeds 8 feet (2438 mm), the volume shall be calculated on the basis of an 8 foot (2438 mm) height.
Related Code Sections
303.2 General Regulations, Closet or Alcove Installations
Central heating furnaces and boilers installed in closets or alcoves shall be listed for such installation. Central heating furnaces not listed ...
2018 Uniform Mechanical Code of Nevada > 3 General Regulations > 303.0 Installation > 303.2 Closet or Alcove Installations
305.7 Building Blocks, Alcoves
If a clear floor space is in an alcove or otherwise confined on all or part of three sides, additional maneuvering clearances complying with Sections ...
Accessible and Usable Buildings and Facilities 2009 of Nevada > 3 Building Blocks > 305 Clear Floor Space > 305.7 Alcoves
126.96.36.199 Installation Requirements, Closets
In all closets and compartments, including those closets housing mechanical equipment, that are not larger than 400 ft 3 (11.3 m 3 ) in size ...
Standard for the Installation of Sprinkler Systems 2016 of Nevada > 8 Installation Requirements > 8.5 Position, Location, Spacing, and Use of Sprinklers > 8.5.5 Obstructions to Sprinkler Discharge > 188.8.131.52 Closets
402.6.1 Plumbing Fixtures and Fixture Fittings, Closet Rings (Closet Flanges)
Closet rings (closet flanges) for water closets or similar fixtures shall be of an approved type and shall be copper alloy, copper, hard lead, cast ...
2018 Uniform Plumbing Code of Nevada > 4 Plumbing Fixtures and Fixture Fittings > 402.0 Installation > 402.6 Flanged Fixture Connections > 402.6.1 Closet Rings (Closet Flanges)
184.108.40.206* Installation Requirements, Closets and Pantries
Sprinklers are not required in clothes closets, linen closets, and pantries within dwelling units in hotels and motels where the area of the space ...
Standard for the Installation of Sprinkler Systems 2016 of Nevada > 8 Installation Requirements > 8.15 Special Situations > 8.15.8 Dwelling Units > 220.127.116.11* Closets and Pantries