// CODE SNIPPET
308.3 Clearances for Indoor Air-Conditioning Equipment
JUMP TO FULL CODE CHAPTER
308.3.2 Equipment Installed in Rooms That Are Not Large in Comparison With the Size of the Equipment
Air-conditioning equipment installed in rooms that are not large in comparison with the size of the equipment, such as alcoves and closets, shall be listed for such installations and installed in accordance with the manufacturer's instructions. Listed clearances shall not be reduced by the protection methods described in Table 308.2, regardless of whether the enclosure is of combustible or noncombustible material.