// CODE SNIPPET
6107.3 Clearance to Combustibles
Related Code Sections
1206.5 Hydronic Piping, Clearance to Combustibles
A pipe in a hydronic piping system in which the exterior temperature exceeds 250°F (121°C) shall have a minimum clearance of 1 inch (25 mm ...
Mechanical Code 2018 of Kansas > 12 Hydronic Piping > 1206 Piping Installation > 1206.5 Clearance to Combustibles
510.9.2 Exhaust Systems, Clearance to Combustibles
Ducts shall have a clearance to combustibles in accordance with Table 510.9.2. Exhaust gases having temperatures in excess of 600°F (316°C) shall ...
Mechanical Code 2018 of Kansas > 5 Exhaust Systems > 510 Hazardous Exhaust Systems > 510.9 Duct Construction > 510.9.2 Clearance to Combustibles
6107.3 Liquefied Petroleum Gases, Clearance to Combustibles
Weeds, grass, brush, trash and other combustible materials shall be kept not less than 10 feet (3048 mm) from LP-gas tanks or containers ...
Fire Code 2018 of Kansas > 61 Liquefied Petroleum Gases > 6107 Safety Precautions and Devices > 6107.3 Clearance to Combustibles
1210.8.3 Hydronic Piping, Clearance From Combustibles
A pipe in a ground-source heat pump piping system having an exterior surface temperature exceeding 250°F (121°C) shall have a minimum clearance ...
Mechanical Code 2018 of Kansas > 12 Hydronic Piping > 1210 Plastic Pipe Ground-Source Heat Pump Loop Systems > 1210.8 Installation > 1210.8.3 Clearance From Combustibles
304.9 General Regulations, Clearances to Combustible Construction
Heat-producing equipment and appliances shall be installed to maintain the required clearances to combustible construction as specified ...
Mechanical Code 2018 of Kansas > 3 General Regulations > 304 Installation > 304.9 Clearances to Combustible Construction