// CODE SNIPPET
1910.304(c)(3) Clearance From Building Openings
JUMP TO FULL CODE CHAPTER
Service conductors installed as open conductors or multiconductor cable without an overall outer jacket shall have a clearance of not less than 914 mm (3.0 ft) from windows that are designed to be opened, doors, porches, balconies, ladders, stairs, fire escapes, and similar locations. However, conductors that run above the top level of a window may be less than 914 mm (3.0 ft) from the window. Vertical clearance of final spans above, or within 914 mm (3.0 ft) measured horizontally of, platforms, projections, or surfaces from which they might be reached shall be maintained in accordance with paragraph (c)(2) of this section.
Overhead service conductors may not be installed beneath openings through which materials may be moved, such as openings in farm and commercial buildings, and may not be installed where they will obstruct entrance to these building openings.
Related Code Sections
1910.304(c)(3) Electrical, Clearance From Building Openings
Service conductors installed as open conductors or multiconductor cable without an overall outer jacket shall have a clearance of not less than 914 ...
OSHA 1910 General Industry > S Electrical > 1910.304 Wiring Design and Protection > 1910.304(c) Outside Conductors, 600 Volts, Nominal, or Less > 1910.304(c)(3) Clearance From Building Openings
1910.265(c)(19)(ii) Special Industries, Clearance
, they shall have a clearance of 6 feet above the driver's foot rest on the carrier, and in no event shall this clearance be less than 12 feet from ...
OSHA 1910 General Industry > R Special Industries > 1910.265 Sawmills > 1910.265(c) Building Facilities, and Isolated Equipment > 1910.265(c)(19) Stationary Tramways and Trestles > 1910.265(c)(19)(ii) Clearance
1910.107(d)(8) Hazardous Materials, Discharge Clearance
Unless the spray booth exhaust duct terminal is from a water-wash spray booth, the terminal discharge point shall be not less than 6 feet from any ...
OSHA 1910 General Industry > H Hazardous Materials > 1910.107 Spray Finishing Using Flammable and Combustible Materials > 1910.107(d) Ventilation > 1910.107(d)(8) Discharge Clearance
1910.176 Materials Handling and Storage, Handling Materials - General
be provided to protect personnel from the hazards of open pits, tanks, vats, ditches, etc. [39 FR 23052, June 27, 1974, as amended at 43 FR 49749 ...
OSHA 1910 General Industry > N Materials Handling and Storage > 1910.176 Handling Materials - General
1910.306(b)(4) Electrical, Clearance
alive shall be a minimum of 762 mm (2.5 ft). Where controls are enclosed in cabinets, the doors shall either open at least 90 degrees or be removable ...
OSHA 1910 General Industry > S Electrical > 1910.306 Specific Purpose Equipment and Installations > 1910.306(b) Cranes and Hoists > 1910.306(b)(4) Clearance