// CODE SNIPPET
307.5.3 Clearance Distances
JUMP TO FULL CODE CHAPTER
Portable outdoor barbecues shall not be stored or used within 10 feet (3048 mm) of any combustible waste, combustible material, or any combustible building surface, including combustible roofs and decks. To the maximum extent feasible, windows, doors and other building openings within 10 feet (3048 mm) of a barbecue in use shall be kept closed. An entrance door shall be closed immediately after entering or exiting the building while the barbecue is in use.
Related Code Sections
308.3.5 General Regulations, Clearance From Supply Ducts
from the furnace plenum. No clearance is necessary beyond this distance ...
NYC Fuel Gas Code 2008 > 3 General Regulations > 308 Clearance Reduction > 308.3 Clearances for Indoor Air-Conditioning Equipment > 308.3.5 Clearance From Supply Ducts
308.4.6 General Regulations, Clearance From Supply Ducts
the furnace plenum. No clearance is necessary beyond this distance ...
NYC Fuel Gas Code 2014 > 3 General Regulations > 308 Clearance Reduction > 308.4 Central-Heating Boilers and Furnaces > 308.4.6 Clearance From Supply Ducts
§27-893 Chimneys and Gas Vents, Clearances
CONNECTOR CLEARANCE[S]* FOR GAS-FIRED EQUIPMENT Equipment Minimum Distances from Combustible Materials (in.) Type B Gas Vent Material Other ...
503.7.7 Chimneys and Vents, Clearances
308.2. TABLE 503.7.7 a CLEARANCES FOR CONNECTORS EQUIPMENT MINIMUM DISTANCE FROM COMBUSTIBLE MATERIAL ...
NYC Fuel Gas Code 2008 > 5 Chimneys and Vents > 503 Venting of Equipment > 503.7 Single-Wall Metal Pipe > 503.7.7 Clearances
503.10.5 Chimneys and Vents, Clearance
in Table 308.2. TABLE 503.10.5 a CLEARANCES FOR CONNECTORS APPLIANCE MINIMUM DISTANCE FROM COMBUSTIBLE MATERIAL Listed ...
NYC Fuel Gas Code 2014 > 5 Chimneys and Vents > 503 Venting of Appliances > 503.10 Vent Connectors for Category I Appliances > 503.10.5 Clearance