// CODE SNIPPET
1926.154(b) Clearance and Mounting
JUMP TO FULL CODE CHAPTER
Temporary heating devices, which are listed for installation with lesser clearances than specified in Table F-4, may be installed in accordance with their approval.
Heaters not suitable for use on wood floors shall not be set directly upon them or other combustible materials. When such heaters are used, they shall rest on suitable heat insulating material or at least 1-inch concrete, or equivalent. The insulating material shall extend beyond the heater 2 feet or more in all directions.
Heaters used in the vicinity of combustible tarpaulins, canvas, or similar coverings shall be located at least 10 feet from the coverings. The coverings shall be securely fastened to prevent ignition or upsetting of the heater due to wind action on the covering or other material.
Related Code Sections
1926.154(b) Fire Protection and Prevention, Clearance and Mounting
Temporary heating devices shall be installed to provide clearance to combustible material not less than the amount shown in Table F-4 ...
OSHA 1926 Construction > F Fire Protection and Prevention > 1926.154 Temporary Heating Devices > 1926.154(b) Clearance and Mounting
1926.403(d)(2) Electrical, Cooling
so that room air flow over such surfaces is not prevented by walls or by adjacent installed equipment. For equipment designed for floor mounting ...
OSHA 1926 Construction > K Electrical > 1926.403 General Requirements > 1926.403(d) Mounting and Cooling of Equipment > 1926.403(d)(2) Cooling
1926.403(d)(1) Electrical, Mounting
Electric equipment shall be firmly secured to the surface on which it is mounted. Wooden plugs driven into holes in masonry, concrete, plaster ...
OSHA 1926 Construction > K Electrical > 1926.403 General Requirements > 1926.403(d) Mounting and Cooling of Equipment > 1926.403(d)(1) Mounting
1926.406(a)(3) Electrical, Clearance
The dimension of the working space in the direction of access to live parts which may require examination, adjustment, servicing, or maintenance while ...
OSHA 1926 Construction > K Electrical > 1926.406 Specific Purpose Equipment and Installations > 1926.406(a) Cranes and Hoists > 1926.406(a)(3) Clearance
1926.66(d)(4) Occupational Health and Environmental Controls, Fan-Rotating Element
clearance between the fan-rotating element and the fan casing to avoid a fire by friction, necessary allowance being made for ordinary expansion ...
OSHA 1926 Construction > D Occupational Health and Environmental Controls > 1926.66 Criteria for Design and Construction of Spray Booths > 1926.66(d) Ventilation > 1926.66(d)(4) Fan-Rotating Element