// CODE SNIPPET
JUMP TO FULL CODE CHAPTER
Clearances around water closets and in toilet compartments shall comply with 604.3.
Clearance around a water closet shall be 60 inches (1525 mm) minimum measured perpendicular from the side wall and 56 inches (1420 mm) minimum measured perpendicular from the rear wall.
The required clearance around the water closet shall be permitted to overlap the water closet, associated grab bars, dispensers, sanitary napkin disposal units, coat hooks, shelves, accessible routes, clear floor space and clearances required at other fixtures, and the turning space. No other fixtures or obstructions shall be located within the required water closet clearance.
EXCEPTION: In residential dwelling units, a lavatory complying with 606 shall be permitted on the rear wall 18 inches (455 mm) minimum from the water closet centerline where the clearance at the water closet is 66 inches (1675 mm) minimum measured perpendicular from the rear wall.
Advisory 604.3.2 Overlap. When the door to the toilet room is placed directly in front of the water closet, the water closet cannot overlap the required maneuvering clearance for the door inside the room.
Related Code Sections
1002.4.4 Recreation Facilities, Clearances
Clearances for wheelchair spaces shall comply with 1002.4.4. EXCEPTIONS : Where provided, securement devices shall be permitted ...
2010 ADA Standards > 10 Recreation Facilities > 1002 Amusement Rides > 1002.4 Wheelchair Spaces in Amusement Rides > 1002.4.4 Clearances
1003.3 Recreation Facilities, Clearances
Clearances at boat slips and on boarding piers at boat launch ramps shall comply with 1003.3. Advisory 1003.3 Clearances. Although the minimum ...
2010 ADA Standards > 10 Recreation Facilities > 1003 Recreational Boating Facilities > 1003.3 Clearances
403.5 Accessible Routes, Clearances
Walking surfaces shall provide clearances complying with 403.5. EXCEPTION : Within employee work areas, clearances on common use circulation ...
505.5 General Site and Building Elements, Clearance
Clearance between handrail gripping surfaces and adjacent surfaces shall be 1 1 / 2 (38 mm) minimum. Figure 505.5 Handrail Clearance ...
603.2 Plumbing Elements and Facilities, Clearances
Clearances shall comply with 603.2. Turning space ...
2010 ADA Standards > 6 Plumbing Elements and Facilities > 603 Toilet and Bathing Rooms > 603.2 Clearances