// CODE SNIPPET
Section P-407 Clay and Concrete Sewer Pipe Joints
JUMP TO FULL CODE CHAPTER
Pre-cast bituminous joints for clay or concrete sewer pipe shall be able to withstand a temperature of 160° F without softening so as to destroy the effectiveness of the joint, and shall not be soluble in any of the wastes carried by the drainage system. Pre-cast bituminous joint material shall:
- Bond firmly to the surface to which it is applied;
- Be accurately cast within the hub and on the spigot;
- Bond securely in the assembled joint; and
- Completely and evenly fill the annular space between the hub and spigot.
Mortar joints for clay sewer pipe or concrete sewer pipe shall be made by packing a closely twisted jute or oakum gasket of suitable size to pass around the pipe and lap at the top, into the annular space between the pipes. The remaining space shall be filled with firmly compacted mortar composed of one part portland cement and three parts mortar sand. The material for the mortar shall be mixed dry; only sufficient water shall be added to make the mixture workable. Lime putty or hydrated lime conforming to Type S of ASTM C207, equal to not more than 25% of the volume of portland cement, shall be permitted in the mortar.
Related Code Sections
Section P-407 Joints, Clay and Concrete Sewer Pipe Joints
Pre-cast bituminous joints for clay or concrete sewer pipe shall be able to withstand a temperature of 160° F without softening so as to destroy ...
P-305.1 Materials, Compliance
ASTM C-425-91 "Specification for Compression Joints for Vitrified Clay Pipe and Fittings" Concrete Sewer Pipe (NonReinforced ...
Philadelphia Plumbing Code > 3 Materials > P-305 Materials for Plumbing Installations > P-305.1 Compliance
R405.1 Foundations, Concrete or Masonry Foundations
is used, an approved filter membrane material shall cover the pipe. The drainage system shall discharge into an approved sewer system or to daylight ...
2018 Philadelphia Residential Code > 4 Foundations > R405 Foundation Drainage > R405.1 Concrete or Masonry Foundations
P3002.2 Sanitary Drainage, Building Sewer
Building sewer piping shall be as shown in Table P3002.2. Forced main sewer piping shall conform to one of the standards for ABS plastic pipe ...
2018 Philadelphia Residential Code > 30 Sanitary Drainage > P3002 Materials > P3002.2 Building Sewer