// CODE SNIPPET
E3905.12.2.2 Clamp Fill
JUMP TO FULL CODE CHAPTER
Where one or more internal cable clamps, whether factory or field supplied, are present in the box, a single volume allowance in accordance with Table E3905.12.2.1 shall be made based on the largest conductor present in the box. An allowance shall not be required for a cable connector having its clamping mechanism outside of the box. A clamp assembly that incorporates a cable termination for the cable conductors shall be listed and marked for use with specific nonmetallic boxes. Conductors that originate within the clamp assembly shall be included in conductor fill calculations provided in Section E3905.12.2.1 as though they entered from outside of the box. The clamp assembly shall not require a fill allowance, but, the volume of the portion of the assembly that remains within the box after installation shall be excluded from the box volume as marked in accordance with Section E3905.12.1.2. [314.16(B)(2)]
Related Code Sections
E3905.12.2.2 Power and Lighting Distribution, Clamp Fill
for use with specific nonmetallic boxes. Conductors that originate within the clamp assembly shall be included in conductor fill calculations provided ...
2015 Michigan Residential Code > 39 Power and Lighting Distribution > E3905 Boxes, Conduit Bodies and Fittings > E3905.12 Number of Conductors in Outlet, Device, and Junction Boxes, and Conduit Bodies > E3905.12.2 Box Fill Calculations > E3905.12.2.2 Clamp Fill
E3611.5 Services, Protection of Ground Clamps and Fittings
Ground clamps or other fittings shall be approved for applications without protection or shall be protected from physical damage by installing them ...
2015 Michigan Residential Code > 36 Services > E3611 Grounding Electrode Conductor Connection to the Grounding Electrodes > E3611.5 Protection of Ground Clamps and Fittings
R506.2.1 Floors, Fill
Fill material shall be free of vegetation and foreign material. The fill shall be compacted to ensure uniform support of the slab, and except where ...
2015 Michigan Residential Code > 5 Floors > R506 Concrete Floors (On Ground) > R506.2 Site Preparation > R506.2.1 Fill
1305.6 Fuel Oil Piping and Storage, Fill Piping
A fill pipe shall terminate outside of a building at a point not less than 2 feet (610 mm) from any building opening at the same or lower level. A ...
2015 Michigan Mechanical Code > 13 Fuel Oil Piping and Storage > 1305 Fuel Oil System Installation > 1305.6 Fill Piping
3304.1 Safeguards During Construction, Excavation and Fill
Excavation and fill for buildings and structures shall be constructed or protected so as not to endanger life or property. Stumps and roots shall ...
2015 Michigan Building Code > 33 Safeguards During Construction > 3304 Site Work > 3304.1 Excavation and Fill