G126.96.36.199 Chilled-Water Pumps (Systems 7, 8, and 11)
Chilled-water systems shall be modeled as primary/secondary systems with constant-flow primary loop and variable-flow secondary loop. For systems with cooling capacity of 300 tons or more, the secondary pump shall be modeled with variable-speed drives and a minimum flow of 25% of the design flow rate. For systems with less than 300 tons cooling capacity, the secondary pump shall be modeled as riding the pump curve. The baseline building constant-volume primary pump power shall be modeled as 9 W/gpm, and the variable-flow secondary pump power shall be modeled as 13 W/gpm at design conditions. For computer room systems using System 11 with an integrated fluid economizer, the baseline building design primary chilled-water pump power shall be increased by 3 W/gpm for flow associated with the fluid economizer.