// CODE SNIPPET
3109.1.1 Changes to the ISPSC
JUMP TO FULL CODE CHAPTER
The following changes shall be made to the ISPSC:
- Add Section 410.2 and related subsections to the ISPSC to read:
410.2 Showers. Showers shall be in accordance with Sections 410.2.1 through 410.2.5.
410.2.1 Deck hand shower or shower spray unit. Not less than one and not greater than half of the total number of showers required by Section 410.1 shall be a hand shower or spray shower unit located on the deck of or at the entrance of each pool.
410.2.2 Anti-scald device. Where heated water is provided to the showers, the shower water supply shall be controlled by an anti-scald device.
401.2.3 Water heater and mixing valve. Bather access to water heaters and thermostatically controlled mixing valves for showers shall be prohibited.
401.2.4 Flow rate. Each showerhead shall have a water flow of not less than 2 gallons per minute (7.6 lpm).
401.2.5 Temperature. At each showerhead, the heated shower water temperature shall not exceed 120°F (49°C) and shall not be less than 90°F (32°C).
- Change the title of Section 609 of the ISPSC to read:
DRESSING AND SANITARY FACILITIES
- Change Section 609.3.1 of the ISPSC to read:
609.3.1 Deck hand shower or shower spray unit. Not less than one and not greater than half of the total number of showers required by Section 609.2 shall be a hand shower or shower spray unit located on the deck of or at the entrance of each pool.
Related Code Sections
3109.1.1 Special Construction, Changes to the ISPSC
The following changes shall be made to the ISPSC: Add Section 410.2 and related subsections to the ISPSC to read: 410.2 Showers. Showers ...
2012 Virginia Construction Code (USBC, Part I) > 31 Special Construction > 3109 Swimming Pools, Swimming Pool Enclosures and Aquatic Recreational Facilities > 3109.1 General > 3109.1.1 Changes to the ISPSC
102.1.1 Administration, Changes
No change shall be made in the use or occupancy of any structure that would place the structure in a different division of the same group ...
2012 Virginia Statewide Fire Prevention Code > 1 Administration > 102 Applicability > 102.1 General > 102.1.1 Changes
Chapter 10 Change of Occupancy
1003.5 Means of Egress, Elevation Change
Where changes in elevation of less than 12 inches (305 mm) exist in the means of egress , sloped surfaces shall be used. Where the slope is greater ...
2012 Virginia Construction Code (USBC, Part I) > 10 Means of Egress > 1003 General Means of Egress > 1003.5 Elevation Change