// CODE SNIPPET
126.96.36.199.1.6* Changes in Occupancy, Use, Process, or Materials
JUMP TO FULL CODE CHAPTER
The evaluation required by 188.8.131.52.1.6 shall not be considered part of the normal inspection, testing, and maintenance required by this Code. [25:184.108.40.206]
The evaluation shall consider factors that include, but are not limited to, the following:
- Occupancy changes such as converting office or production space into warehousing
- Process or material changes such as metal stamping to molded plastics
- Building revisions such as relocated walls, added mezzanines, and ceilings added below sprinklers
- Removal of heating systems in spaces with piping subject to freezing
- Changes to the storage method, arrangement, height, or commodities
- Changes in water supplies
Related Code Sections
220.127.116.11.1.6* Fire Protection Systems, Changes in Occupancy, Use, Process, or Materials
The property owner or designated representative shall not make changes in the occupancy, the use or process, or the materials used or stored ...
Fire Code 2018 of West Virginia > 13 Fire Protection Systems > 13.3 Automatic Sprinklers > 13.3.3 Inspection, Testing, and Maintenance > 18.104.22.168 General Requirements > 22.214.171.124.1 Responsibility of the Property Owner or Designated Representative > 126.96.36.199.1.6* Changes in Occupancy, Use, Process, or Materials
188.8.131.52.5 Marijuana Growing, Processing, or Extraction Facilities, Change of Extraction Medium
Where the medium of extraction or solvent is changed from the material indicated in the technical report or as required by the manufacturer ...
Fire Code 2018 of West Virginia > 38 Marijuana Growing, Processing, or Extraction Facilities > 38.6* Processing or Extraction > 38.6.1 General > 184.108.40.206 Systems, Equipment, and Processes > 220.127.116.11.5 Change of Extraction Medium
66.17.15 Flammable and Combustible Liquids, Management of Operations Hazards
a review shall include, but are not limited to, the following: When changes occur in the materials in process When changes occur in process ...
Fire Code 2018 of West Virginia > 66 Flammable and Combustible Liquids > 66.17 Processing Facilities > 66.17.15 Management of Operations Hazards
Section 1205 Historic Buildings, Change of Occupancy
Regardless of occupancy or use group, roof-covering materials not less than Class C, when ...