// CODE SNIPPET
3406.4.10.5.1 Cargo Tank Loading Racks
JUMP TO FULL CODE CHAPTER
A fire extinguishing system shall be provided over and under each cargo tank loading position. At least one remote control valve shall be provided to control the extinguishing agent for each three loading positions. Piping systems shall be installed so they can be thoroughly drained. The fire extinguishing system shall be sized to provide protection for the three largest adjacent loading positions.