A procedure room with a minimum clear floor area of 400 square feet (37.16 m2) for the procedure room in addition to spaces for control, monitoring and recording equipment, and x-ray power and controls, and a minimum of one scrub sink for each catheterization laboratory. This space does not include the control room.
Where electrophysiology studies are performed, dedicated space and equipment for emergency resuscitation and stabilization shall be immediately accessible to the procedure room.
A control room or area shall be provided. A view window permitting full view of the patient from the control console shall be provided.
An equipment space or enclosure large enough to contain x-ray transformers, power modules, and associated electronics and electrical gear shall be provided.
Appropriate areas shall be provided for male and female staff working within the surgical service space. The areas shall contain lockers, showers, toilets, lavatories equipped for handwashing, and space for donning surgical attire. These areas shall be arranged to ensure a traffic pattern so that personnel entering from outside the service space can enter, change their clothing, and move directly into the cardiac catheterization service space. The staff change area may be combined with the surgical staff change area.
A patient preparation, holding, and recovery area or room shall be provided and arranged to provide visual observation before and after the procedure. This may occur in a unit outside of the catheterization service space.
A clean utility room shall be provided. If the room is used for preparing patient care items, it shall contain a work counter and handwashing fixture. If the room is used only for storage and holding of clean and sterile supply materials, the work counter and handwashing fixtures shall be permitted to be omitted. The clean utility may be shared with an adjacent surgical unit.
A soiled utility room shall be provided which shall contain a handwashing fixture and a clinical sink (or equivalent flushing rim fixtures). When the room is used for temporary holding or soiled materials, the clinical sink and handwashing fixture shall be permitted to be omitted. The soiled utility may be shared with an adjacent surgical unit.