// CODE SNIPPET
18.104.22.168.3.9* Carbon Dioxide
Go To Full Code Chapter
The vapor phase of carbon dioxide shall be not less than 99.5 percent carbon dioxide. [10:22.214.171.124.1]
The water content shall be not more than 60 parts per million (ppm) by weight at —52°F (—47°C) dew point. [10:126.96.36.199.2]
Oil content shall not exceed 10 ppm by weight. [10:188.8.131.52.3]
Related Code Sections
184.108.40.206.3.9* Fire Protection Systems, Carbon Dioxide
The vapor phase of carbon dioxide shall be not less than 99.5 percent carbon dioxide. [10:220.127.116.11.1 ...
38.6.4 Marijuana Growing, Processing, or Extraction Facilities, Carbon Dioxide Extraction
Marijuana extraction facilities using carbon dioxide solvents shall comply with 38.6.1 and 38.6.4 ...
904.12.3 Fire Protection Systems, Carbon Dioxide Systems
Where carbon dioxide systems are used, there shall be a nozzle at the top of the ventilating duct. Additional nozzles that are symmetrically arranged ...
908.7 Fire Protection Systems, Carbon Dioxide (CO2) Systems
Emergency alarm systems in accordance with the NFPA 1 2018 Edition shall be provided where required for compliance with Section 5307.5 of the NFPA 1 ...
18.104.22.168 Compressed Gases and Cryogenic Fluids, Insulated Liquid Carbon Dioxide Systems
Insulated liquid carbon dioxide systems shall be in accordance with Chapter 13 of NFPA 55. [55:7.1.3] ...