// CODE SNIPPET
304.3.3 Capacity Exceeding 200 Gallons
Go To Full Code Chapter
Dumpsters and other containers with an individual capacity exceeding 200 gallons (0.76 m3) shall not be stored indoors, and shall not be stored outdoors within 5 feet (1524 mm) of combustible walls, openings or combustible roof eave lines.
- Dumpsters or containers in areas protected throughout by a sprinkler system.
- Storage in a building or structure of Type I or Type IIA construction or other construction with an equivalent fire rating, where such building or structure is located not less than 10 feet (3048 mm) from other buildings or structures and used exclusively for container or dumpster storage.
Related Code Sections
§27-829 Heating and Combustion Equipment, Location of Tanks
) Outside of buildings, above ground. (1) Storage tanks of a capacity greater than two hundred seventy-five gallons located outside of buildings above ...
1305.15.2 Fuel-Oil Piping and Storage, Capacity
The capacity of nonmetallic fuel-oil storage tanks shall be not less than 60 gallons (227.1 L) and not more than 660 gallons (2498.4 L) ...
§28-405.2 Licensing and Registration of Businesses, Trades and Occupations Engaged in Building Work, Classification
and any other extensions to the boom, not exceeding 200 feet in length (60 960 mm) with a manufacturer's rated capacity of 50 tons (51 t) or less ...
*§28-405.2 Licensing and Registration of Businesses, Trades and Occupations Engaged in Building Work, Classification
, not exceeding 200 feet in length (60 960 mm) with a manufacturer's rated capacity of 50 tons (51 t) or less; Class C2: License to operate boom trucks ...
1009.2 Boilers, Water Heaters and Pressure Vessels, Closed-Type Expansion Tanks
CLOSED-TYPE EXPANSION TANK SIZING SYSTEM VOLUME IN GALLONS TANK CAPACITIES IN GALLONS Pressurized Diaphragm Type Nonpressurized Type ...