// CODE SNIPPET
392.56 Cable Splices
Related Code Sections
392.56 Wiring Methods and Materials, Cable Splices
Cable splices made and insulated by approved methods shall be permitted to be located within a cable tray, provided they are accessible. Splices ...
National Electrical Code 2020 of Minnesota > 3 Wiring Methods and Materials > 392 Cable Trays > 392.56 Cable Splices
(D) Equipment for General Use, Splices
All heating cables, the splice between the heating cable and nonheating leads, and 75-mm (3-in.) minimum of the nonheating lead at the splice shall ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 424 Fixed Electric Space-Heating Equipment > 424.41 Ceiling Installation of Heating Cables on Dry Board, in Plaster, and on Concrete > (D) Splices
(A) Special Occupancies, Stage Set Wiring
Where subject to physical damage, such wiring shall be listed extra-hard usage flexible cords and cables. Splices or taps in cables shall be permitted ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 530 Motion Picture and Television Studios and Similar Locations > 530.12 Portable Wiring > (A) Stage Set Wiring
(1) Special Conditions, In Raceways, Exposed on Ceilings or Sidewalls, or Fished in Concealed Spaces
Cable splices or terminations shall be made in listed fittings, boxes, enclosures, fire alarm devices, or utilization equipment. Where installed ...
National Electrical Code 2020 of Minnesota > 7 Special Conditions > 760 Fire Alarm Systems > 760.130 Wiring Methods and Materials on Load Side of the PLFA Power Source > (B) PLFA Wiring Methods and Materials > (1) In Raceways, Exposed on Ceilings or Sidewalls, or Fished in Concealed Spaces
(D) Wiring Methods and Materials, Splices
Direct burial cables shall be permitted to be spliced or tapped without the use of splice boxes, provided they are installed using materials suitable ...
National Electrical Code 2020 of Minnesota > 3 Wiring Methods and Materials > 300 General Requirements for Wiring Methods and Materials > 300.50 Underground Installations > (D) Splices