// CODE SNIPPET
1308.7.8 Bypass Piping
JUMP TO FULL CODE CHAPTER
Valved and regulated bypasses shall be permitted to be placed around gas line pressure regulators where continuity of service is imperative. [NFPA 54:5.8.7]
Related Code Sections
1308.7.8 Fuel Gas Piping, Bypass Piping
Valved and regulated bypasses shall be permitted to be placed around gas line pressure regulators where continuity of service is imperative. [NFPA 54 ...
Los Angeles Mechanical Code > 13 Fuel Gas Piping > 1308.0 Gas Piping System Design, Materials, and Components > 1308.7 Gas Pressure Regulators > 1308.7.8 Bypass Piping
928.4 Installation of Specific Appliances, Bypass Valves
Where an integral bypass system is not provided as a part of the pool heater, a bypass line and valve shall be installed between the inlet and outlet ...
Los Angeles Mechanical Code > 9 Installation of Specific Appliances > 928.0 Pool Heaters > 928.4 Bypass Valves
1214.5.1 Hydronics, Differential Pressure Bypass Valve
Where a differential pressure bypass valve is used for the purpose specified in Section 1214.5, it shall be installed and adjusted to provide bypass ...
Los Angeles Mechanical Code > 12 Hydronics > 1214.0 Pressure and Flow Controls > 1214.5 Differential Pressure Regulation > 1214.5.1 Differential Pressure Bypass Valve
3002.10 Elevators and Conveying Systems, Photoelectric Tube Bypass Switch
Elevators equipped with photoelectric tube devices which control the closing of automatic, power-operated car or hoistway doors, or both, shall have ...
Los Angeles Building Code > 30 Elevators and Conveying Systems > 3002 Hoistway Enclosures > 3002.10 Photoelectric Tube Bypass Switch
909.20.6 Fire Protection Systems, Components Bypassing Weekly Test
Where components of the smoke control system are bypassed by the preprogrammed weekly test required by Section 909.12.1, such components shall ...
Los Angeles Fire Code > 9 Fire Protection Systems > 909 Smoke Control Systems > 909.20 Maintenance > 909.20.6 Components Bypassing Weekly Test