// CODE SNIPPET
E3908.9.1.1 By Means of an Equipment Grounding Conductor
JUMP TO FULL CODE CHAPTER
By means of an equipment grounding conductor run with the power supply conductors in a cable assembly or flexible cord properly terminated in a grounding-type attachment plug with 1 fixed grounding contact. [250.138(A)]
Exception: The grounding contacting pole of grounding-type plug-in ground-fault circuit interrupters may be of the movable, self-restoring type on circuits operating at not over 150 volts between any 2 conductors or over 150 volts between any conductor and ground. [250.138(A) Exception]
Related Code Sections
E3908.9.1.1 Power and Lighting Distribution, By Means of an Equipment Grounding Conductor
By means of an equipment grounding conductor run with the power supply conductors in a cable assembly or flexible cord properly terminated ...
2015 Michigan Residential Code > 39 Power and Lighting Distribution > E3908 Grounding > E3908.9 Equipment Fastened in Place or Connected by Permanent Wiring Methods > E3908.9.1 Cord-And-Plug-Connected Equipment > E3908.9.1.1 By Means of an Equipment Grounding Conductor
E3607.3.1 Services, Equipment Grounding Conductor
disconnecting means and to the grounding electrode(s). The equipment grounding conductor shall be used for grounding or bonding of equipment, structures ...
2015 Michigan Residential Code > 36 Services > E3607 System Grounding > E3607.3 Buildings or Structures Supplied by Feeder(s) or Branch Circuit(s) > E3607.3.1 Equipment Grounding Conductor
E4001.11.1 Devices and Luminaries, Faceplate Grounding
Snap switches, including dimmer and similar control switches, shall be connected to an equipment grounding conductor and shall provide a means ...
2015 Michigan Residential Code > 40 Devices and Luminaries > E4001 Switches > E4001.11 Snap Switch Faceplates > E4001.11.1 Faceplate Grounding
E3406.13 General Requirements, Connection of Grounding and Bonding Equipment
The connection of equipment grounding conductors, grounding electrode conductors and bonding jumpers shall be in accordance with Sections E3406.13.1 ...
2015 Michigan Residential Code > 34 General Requirements > E3406 Electrical Conductors and Connections > E3406.13 Connection of Grounding and Bonding Equipment
E3407.2 General Requirements, Equipment Grounding Conductors
Equipment grounding conductors of sizes 6 AWG and smaller shall be identified by a continuous green color or a continuous green color with one ...
2015 Michigan Residential Code > 34 General Requirements > E3407 Conductor and Terminal Identification > E3407.2 Equipment Grounding Conductors