// CODE SNIPPET
1102.4 Building Storm Sewer Pipe
JUMP TO FULL CODE CHAPTER
Building storm sewer pipe shall conform to one of the standards listed in Table 1102.4.
BUILDING STORM SEWER PIPE
|Acrylonitrile butadiene styrene (ABS) plastic pipe in IPS diameters, including Schedule 40, DR 22 (PS 200) and DR 24 (PS 140); with a solid, cellular core or composite wall.||ASTM D2661; ASTM F628; ASTM F1488; CSA B181.1; CSA B182.1|
|Cast-iron pipe||ASTM A74; ASTM A888; CISPI 301|
|Concrete pipe||ASTM C14; ASTM C76; CSA A257.1M; CSA A257.2M|
|Copper or copper-alloy tubing (Type K, L, M or DWV)||ASTM B75; ASTM B88; ASTM B251; ASTM B306|
|Polyethylene (PE) plastic pipe||ASTM F667;ASTM F2306/F2306M; ASTM F2648/F2648M|
|Polypropylene (PP) pipe||ASTM F2881; CSA B182.13|
|Polyvinyl chloride (PVC) plastic pipe (Type DWV, SDR26, SDR35, SDR41, PS50 or PS100) in IPS diameters, including Schedule 40, DR 22 (PS 200) and DR 24 (PS 140); with a solid, cellular core or composite wall.||ASTM D2665; ASTM D3034; ASTM F891; ASTM F1488; CSA B182.4; CSA B181.2; CSA B182.2|
|Vitrified clay pipe||ASTM C4; ASTM C700|
|Stainless steel drainage systems, Type 316L||ASME A112.3.1|
Related Code Sections
1102.4 Storm Drainage, Building Storm Sewer Pipe
Building storm sewer pipe shall conform to one of the standards listed in Table 1102.4. TABLE 1102.4 BUILDING STORM SEWER PIPE MATERIAL ...
Plumbing Code 2018 of Kansas > 11 Storm Drainage > 1102 Materials > 1102.4 Building Storm Sewer Pipe
Section 1103 Storm Drainage, Traps
sewer or the public sewer . Leaders and storm drains connected to a building storm sewer shall not be required to be trapped ...
Section 703 Sanitary Drainage, Building Sewer
Where a building sewer or building drain is installed on filled or unstable ground, the drainage pipe shall conform ...
Section P3302 Storm Drainage, Subsoil Drains
B182.1; CSA B182.6; CSA B182.8 Polyvinyl chloride (PVC) plastic pipe (type sewer pipe, SDR 35, PS25, PS50 or PS100) ASTM D2729; ASTM D3034; ASTM ...