// CODE SNIPPET
11.1.7 Building Disconnect
JUMP TO FULL CODE CHAPTER
The disconnecting means shall be maintained accessible to the fire department.
Each disconnecting means shall be legibly marked to indicate its purpose unless located and arranged so the purpose is evident. The marking shall be of sufficient durability to withstand the environment involved. [70:110.22(A)]
Related Code Sections
11.1.7 Building Services, Building Disconnect
Means shall be provided for the fire department to disconnect the electrical service to a building, structure, or facility when the electrical ...
Fire Code 2018 of West Virginia > 11 Building Services > 11.1 Electrical Fire Safety > 11.1.7 Building Disconnect
545.5 Special Occupancies, Supply Conductors
to the service or building disconnecting means conductors ...
National Electrical Code 2017 of West Virginia > 5 Special Occupancies > 545 Manufactured Buildings > 545.5 Supply Conductors
225.38 Wiring and Protection, Disconnect Construction
or structure disconnecting means shall simultaneously disconnect all ungrounded supply conductors that it controls from the building or structure wiring system ...
National Electrical Code 2017 of West Virginia > 2 Wiring and Protection > 225 Outside Branch Circuits and Feeders > 225.38 Disconnect Construction
(1) Wiring and Protection, Supplied by a Feeder or Branch Circuit
or structure disconnecting means and to the grounding electrode(s). The grounding electrode(s) shall also be connected to the building or structure disconnecting ...
National Electrical Code 2017 of West Virginia > 2 Wiring and Protection > 250 Grounding and Bonding > 250.32 Buildings or Structures Supplied by a Feeder(s) or Branch Circuit(s) > (C) Ungrounded Systems > (1) Supplied by a Feeder or Branch Circuit
(5) Special Conditions, Outdoor Generator Sets
means is located within sight of the building or structure supplied, an additional disconnecting means shall not be required where ungrounded conductors ...
National Electrical Code 2017 of West Virginia > 7 Special Conditions > 701 Legally Required Standby Systems > 701.12 General Requirements > (B) Generator Set > (5) Outdoor Generator Sets