// CODE SNIPPET
JUMP TO FULL CODE CHAPTER
All joint surfaces shall be cleaned. An approved flux shall be applied where required. The joint shall be brazed with a filler metal conforming to AWS A5.8.
Mechanical joints shall be installed in accordance with the manufacturer's instructions.
Threads shall conform to ASME B1.20.1. Pipe-joint compound or tape shall be applied on the male threads only.
Related Code Sections
P3003.5 Sanitary Drainage, Brass
Joints between brass pipe or fittings shall comply with Sections P3003.5.1 through P3003.5.3 ...
Residential Code 2012 of South Holland > 30 Sanitary Drainage > P3003 Joints and Connections > P3003.5 Brass
1203.5 Hydronic Piping, Brass Pipe
Joints between brass pipe or fittings shall be brazed, mechanical, threaded or welded joints conforming to Section 1203.3 ...
Mechanical Code 2012 of South Holland > 12 Hydronic Piping > 1203 Joints and Connections > 1203.5 Brass Pipe
1303.4 Fuel Oil Piping and Storage, Brass Pipe
Joints between brass pipe or fittings shall be brazed, mechanical, threaded or welded joints complying with Section 1303.3 ...
Mechanical Code 2012 of South Holland > 13 Fuel Oil Piping and Storage > 1303 Joints and Connections > 1303.4 Brass Pipe
403.4.3 Gas Piping Installations, Copper and Brass
Copper and brass pipe shall not be used if the gas contains more than an average of 0.3 grains of hydrogen sulfide per 100 standard cubic feet of gas ...
Fuel Gas Code 2012 of South Holland > 4 Gas Piping Installations > 403 (IFGS) Piping Materials > 403.4 Metallic Pipe > 403.4.3 Copper and Brass
1107.5.2 Refrigeration, Copper and Brass Pipe
Standard iron-pipe size, copper and red brass (not less than 80-percent copper) pipe shall conform to ASTM B 42 and ASTM B 43 ...
Mechanical Code 2012 of South Holland > 11 Refrigeration > 1107 Refrigerant Piping > 1107.5 Materials for Refrigerant Pipe and Tubing > 1107.5.2 Copper and Brass Pipe