// CODE SNIPPET
N1184.108.40.206 (R303.1.1.1) Blown or Sprayed Roof/ Ceiling Insulation
JUMP TO FULL CODE CHAPTER
The thickness of blown-in or sprayed roof/ceiling insulation (fiberglass or cellulose) shall be written in inches (mm) on markers that are installed at least one for every 300 square feet (28 m2) throughout the attic space. The markers shall be affixed to the trusses or joists and marked with the minimum initial installed thickness with numbers a minimum of 1 inch (25 mm) in height. Each marker shall face the attic access opening. Spray polyurethane foam thickness and installed R-value shall be listed on certification provided by the insulation installer.
Related Code Sections
N1220.127.116.11 [RE] Energy Efficiency, (R303.1.1.1) Blown or Sprayed Roof/ Ceiling Insulation
The thickness of blown-in or sprayed roof/ceiling insulation (fiberglass or cellulose) shall be written in inches (mm) on markers that are installed ...
2015 Michigan Residential Code > 11 [RE] Energy Efficiency > N1101 General > N1101.12 (R303.1) Identification > N1101.12.1 (R303.1.1) Building Thermal Envelope Insulation > N118.104.22.168 (R303.1.1.1) Blown or Sprayed Roof/ Ceiling Insulation
22.214.171.124 Building Envelope, Loose-Fill Insulation Limitation
Open-blown or poured loose-fill insulation shall not be used in attic roof spaces when the slope of the ceiling is more than three in twelve ...
Energy Standard for Buildings Except Low-Rise Residential Buildings 2013 of Michigan > 5 Building Envelope > 5.8 Product Information and Installation Requirements > 5.8.1 Insulation > 126.96.36.199 Loose-Fill Insulation Limitation
R302.10.1 Building Planning, Insulation
Insulation materials, including facings, such as vapor retarders and vapor-permeable membranes installed within floor-ceiling assemblies, roof ...
2015 Michigan Residential Code > 3 Building Planning > R302 Fire-Resistant Construction > R302.10 Flame Spread Index and Smoke-Developed Index for Insulation > R302.10.1 Insulation
188.8.131.52 General Requirements for Storage, Clearance to Ceiling
to underside of the ceiling or roof structure, the clearance to ceiling shall be measured from the top of storage to the bottom of the insulation and shall ...
Standard for the Installation of Sprinkler Systems 2013 of Michigan > 12 General Requirements for Storage > 12.1 General > 12.1.3* Building and Storage Height > 184.108.40.206 Clearance to Ceiling
220.127.116.11.3 Installation Requirements, Peaked Roofs and Ceilings
Unless the requirements of 18.104.22.168.3.2 or 22.214.171.124.3.3 are met, sprinklers under or near the peak of a roof or ceiling shall have deflectors located ...
Standard for the Installation of Sprinkler Systems 2013 of Michigan > 8 Installation Requirements > 8.6 Standard Pendent and Upright Spray Sprinklers > 8.6.4 Deflector Position (Standard Pendent and Upright Spray Sprinklers) > 126.96.36.199 Distance Below Ceilings > 188.8.131.52.3 Peaked Roofs and Ceilings