// CODE SNIPPET
JUMP TO FULL CODE CHAPTER
Supports for bell-and-spigot cast iron pipe shall be a maximum 7 feet on centers.
Related Code Sections
P-602.1.1 Pipe Supports, Bell-And-Spigot
Supports for bell-and-spigot cast iron pipe shall be a maximum 7 feet on centers ...
Philadelphia Plumbing Code > 6 Pipe Supports > P-602 Horizontal Piping > P-602.1 Spacing > P-602.1.1 Bell-And-Spigot
P-305.5 Materials, Pipes and Joints Permitted
-and-Spigot (lead and oakum), No-Hub Coupling, Neoprene Gasket Ductile Iron Bell-and-Spigot, Neoprene Gasket, Mechanical Joint ...
Philadelphia Plumbing Code > 3 Materials > P-305 Materials for Plumbing Installations > P-305.5 Pipes and Joints Permitted
P-403.1 Joints, Cast Iron Soil Pipe
Cast iron-bell-and-spigot soil pipe shall be firmly packed with oakum or hemp and filled with molten lead not less than 1-inch deep which shall ...
1810.3.9.5 Soils and Foundations, Belled Drilled Shafts
Where drilled shafts are belled at the bottom, the edge thickness of the bell shall be not less than that required for the edge of footings. Where ...
2018 Philadelphia Building Code > 18 Soils and Foundations > 1810 Deep Foundations > 1810.3 Design and Detailing > 1810.3.9 Cast-In-Place Deep Foundations > 1810.3.9.5 Belled Drilled Shafts
Section P-305 Materials, Materials for Plumbing Installations
Threaded or Welding on large size gas piping Cast Iron Soil Pipe and Fittings Bell-and-Spigot (lead and oakum), No-Hub Coupling ...