// CODE SNIPPET
Section P-505 Bath Traps
JUMP TO FULL CODE CHAPTER
A minimum 14-inch wide and 28-inch high panel shall be provided to afford access to the bath trap. It shall be located on the wall behind the end of the bath tub where the drain outlet is located. The access panel shall be a minimum 12" x 18" when located in the ceiling below.
Exceptions: Access panels shall not be required for the following:
- Buildings of Use Group R-1.
- Buildings of Use Group R-2 containing more than 8 stories of dwelling units.
- Where trap joints are soldered, solvent cemented or screwed so as to form a solid connection.
Access panels which are installed within fireresistance rated assemblies shall be labeled doors of the required fireresistance rating. Installation in stairway enclosures is prohibited.
Related Code Sections
Section P-505 Traps, Cleanouts, Interceptors, and Backwater Valves, Bath Traps
Traps of 17-gauge are not permitted to be used as bath traps. The minimum size trap shall be 1-1/2 inches inside nominal diameter and shall have ...
Philadelphia Plumbing Code > 5 Traps, Cleanouts, Interceptors, and Backwater Valves > P-505 Bath Traps
Section 1103 Storm Drainage, Traps
Leaders and storm drains connected to a combined sewer shall be trapped. Individual storm water traps shall be installed on the storm water drain ...
1302.3 Nonpotable Water Systems, Traps
Traps serving fixtures and devices discharging waste water to on-site nonpotable water reuse systems shall comply with Section 1002.4 ...
Plumbing Code 2018 of Philadelphia > 13 Nonpotable Water Systems > 1302 On-Site Nonpotable Water Reuse Systems > 1302.3 Traps