// CODE SNIPPET
2510.5.3 Backing Not Required
Related Code Sections
2510.5.3 Gypsum Board, Gypsum Panel Products and Plaster, Backing Not Required
Wire backing is not required under expanded metal lath or paperbacked wire fabric lath ...
Building Code 2018 of Illinois > 25 Gypsum Board, Gypsum Panel Products and Plaster > 2510 Lathing and Furring for Cement Plaster (Stucco) > 2510.5 Backing > 2510.5.3 Backing Not Required
380.12 Wiring Methods and Materials, Uses Not Permitted
A multioutlet assembly shall not be installed as follows: Where concealed, except that it shall be permissible to surround the back and sides ...
National Electrical Code 2017 of Illinois > 3 Wiring Methods and Materials > 380 Multioutlet Assembly > 380.12 Uses Not Permitted
415.6 Special Detailed Requirements Based on Occupancy and Use, Fire Separation Distance
Regardless of any other provisions, buildings containing Group H occupancies shall be set back to the minimum fire separation distance as set ...
Building Code 2018 of Illinois > 4 Special Detailed Requirements Based on Occupancy and Use > 415 Groups H-1, H-2, H-3, H-4 and H-5 > 415.6 Fire Separation Distance
(A) Special Occupancies, Not Covered
A recreational vehicle not used for the purposes as defined in 551.2 shall not be required to meet the provisions of Part IV pertaining to the number ...
National Electrical Code 2017 of Illinois > 5 Special Occupancies > 551 Recreational Vehicles and Recreational Vehicle Parks > 551.4 General Requirements > (A) Not Covered
(C) Special Conditions, Not Functioning
To indicate that the battery charger is not functioning. Informational Note: For signals for generator sets, see NFPA 110-2013, Standard ...
National Electrical Code 2017 of Illinois > 7 Special Conditions > 701 Legally Required Standby Systems > 701.6 Signals > (C) Not Functioning