// CODE SNIPPET
7188.8.131.52 Attachment of Finishes
JUMP TO FULL CODE CHAPTER
Installation of finishes shall be as follows:
- Gypsum wallboard and gypsum lath applied to concrete masonry or concrete walls shall be secured to wood or steel furring members spaced not more than 16 inches (406 mm) on center (o.c.).
- Gypsum wallboard shall be installed with the long dimension parallel to the furring members and shall have all joints finished.
- Other aspects of the installation of finishes shall comply with the applicable provisions of Chapters 7 and 25.
Related Code Sections
7184.108.40.206 Fire and Smoke Protection Features, Attachment of Finishes
Installation of finishes shall be as follows: Gypsum wallboard and gypsum lath applied to concrete masonry or concrete walls shall be secured ...
Building Code 2018 of Illinois > 7 Fire and Smoke Protection Features > 722 Calculated Fire Resistance > 722.3 Concrete Masonry > 722.3.2 Concrete Masonry Walls > 7220.127.116.11 Attachment of Finishes
230.26 Wiring and Protection, Point of Attachment
in 230.9 and 230.24. In no case shall this point of attachment be less than 3.0 m (10 ft) above finished grade ...
National Electrical Code 2017 of Illinois > 2 Wiring and Protection > 230 Services > 230.26 Point of Attachment
Section 805 Interior Finishes, Combustible Materials in Types I and II Construction
Wood finish flooring is permitted to be attached directly ...
Building Code 2018 of Illinois > 8 Interior Finishes > 805 Combustible Materials in Types I and II Construction
(A) Wiring Methods and Materials, Nonmetallic Extensions
between each two adjacent outlets supplied. An extension shall be attached to only woodwork or plaster finish and shall not be in contact with any metal ...
National Electrical Code 2017 of Illinois > 3 Wiring Methods and Materials > 382 Nonmetallic Extensions > 382.30 Securing and Supporting > (A) Nonmetallic Extensions
(D) Wiring and Protection, Screw Shell Devices With Leads
For screw shell devices with attached leads, the conductor attached to the screw shell shall have a white or gray finish. The outer finish ...
National Electrical Code 2017 of Illinois > 2 Wiring and Protection > 200 Use and Identification of Grounded Conductors > 200.10 Identification of Terminals > (D) Screw Shell Devices With Leads