// CODE SNIPPET
H 701.7 Arch and Dome
JUMP TO FULL CODE CHAPTER
The arch or dome of a seepage pit shall be permitted to be constructed in one of three ways:
- Approved-type hard-burned clay brick or solid concrete brick or block laid in cement mortar.
- Approved brick or block laid dry. In both of the above methods, an approved cement mortar covering of not less than 2 inches (51 mm) in thickness shall be applied, said covering to extend not less than 6 inches (152 mm) beyond the sidewalls of the pit.
- Approved-type one or two-piece reinforced concrete slabs of not less than 2500 lb/in2 (1 757 672 kg/m2) minimum compressive strength, not less than 5 inches (127 mm) thick, and designed to support an earth load of not less than 400 pounds per square foot (lb/ft2) (1953 kg/m2). Each such cover shall be provided with a 9 inch (229 mm) minimum inspection hole with plug or cover and shall be coated on the underside with an approved bituminous or other nonpermeable protective compound.
Related Code Sections
H 701.7 Private Sewage Disposal Systems, Arch and Dome
The arch or dome of a seepage pit shall be permitted to be constructed in one of three ways: Approved-type hard-burned clay brick or solid ...
Uniform Plumbing Code 2018 of Nevada > H Private Sewage Disposal Systems > H 701.0 Seepage Pits > H 701.7 Arch and Dome
1607.13.2.1 Structural Design, Ordinary Roofs, Awnings and Canopies
of rise per foot (for SI: F = 0.12 × slope, with slope expressed as a percentage), or for an arch or dome, the rise-to-span ratio multiplied by 32 ...
Building Code 2018 of Nevada > 16 Structural Design > 1607 Live Loads > 1607.13 Roof Loads > 1607.13.2 General > 1607.13.2.1 Ordinary Roofs, Awnings and Canopies
1607.12.2.1 Structural Design, Ordinary Roofs, Awnings and Canopies
expressed as a percentage), or for an arch or dome, the rise-to-span ratio multiplied by 32. ...
Building Code 2012 of Nevada > 16 Structural Design > 1607 Live Loads > 1607.12 Roof Loads > 1607.12.2 General > 1607.12.2.1 Ordinary Roofs, Awnings and Canopies
705.5 Communication Elements and Features, Truncated Domes
Detectable warning surfaces shall have truncated domes complying with Section 705.5. FIG. 705.5 TRUNCATED DOME SIZE AND SPACING ...
Accessible and Usable Buildings and Facilities 2009 of Nevada > 7 Communication Elements and Features > 705 Detectable Warnings > 705.5 Truncated Domes
1102.2 Storm Drainage, Dome Strainers Required
Roof drains shall have domed strainers. Exception: Roof drain strainers for use on sun decks, parking decks, and similar areas that are normally ...
Uniform Plumbing Code 2018 of Nevada > 11 Storm Drainage > 1102.0 Roof Drains > 1102.2 Dome Strainers Required