// CODE SNIPPET
5704.1.1 Application of Sprinkler Protection Tables
JUMP TO FULL CODE CHAPTER
Tables 5704.3.6.3(4) through 5704.3.6.3(8) shall only apply to liquids stored in metal containers and tanks. For liquids stored in nonmetallic containers, nonmetallic portable tanks or rigid nonmetallic intermediate bulk containers, sprinkler protection shall be designed and installed in accordance with criteria based on full-scale fire testing conducted at an approved testing laboratory or based on other nationally recognized fire safety standards approved by the code official.
Related Code Sections
5704.1.1 Flammable and Combustible Liquids, Application of Sprinkler Protection Tables
containers, nonmetallic portable tanks or rigid nonmetallic intermediate bulk containers, sprinkler protection shall be designed and installed in accordance ...
Minnesota Fire Code 2015 > 57 Flammable and Combustible Liquids > 5704 Storage > 5704.1 General > 5704.1.1 Application of Sprinkler Protection Tables
13.3.1 Protection of Miscellaneous and Low-Piled Storage, General
In-rack sprinklers required by Table 13.2.1 shall meet the requirements of this section and the applicable storage protection and arrangement ...
Standard for the Installation of Sprinkler Systems 2016 of Minnesota > 13 Protection of Miscellaneous and Low-Piled Storage > 13.3 In-Rack Sprinklers > 13.3.1 General
23.6* Plans and Calculations, Exposure Protection Sprinkler Systems
Exposure protection sprinkler systems shall be hydraulically calculated using Table 23.6.1 based on severity of exposure as indicated by a relative ...
Standard for the Installation of Sprinkler Systems 2016 of Minnesota > 23 Plans and Calculations > 23.6* Exposure Protection Sprinkler Systems
188.8.131.52.1 Special Occupancy Requirements,
Sprinkler protection for Class 2 oxidizers shall be designed in accordance with Table 184.108.40.206.1. [ 400: 220.127.116.11.4.1] Table 18.104.22.168.1 Ceiling ...
Standard for the Installation of Sprinkler Systems 2016 of Minnesota > 22 Special Occupancy Requirements > 22.37 Hazardous Materials Code > 22.37.1 Design Requirements > 22.214.171.124 Indoor Storage of Oxidizer Solids and Liquids > 126.96.36.199.1
Section 3207 High-Piled Combustible Storage, Solid-Piled and Shelf Storage
Where automatic sprinklers are required by Table 3206.2, an approved automatic sprinkler system shall be installed throughout the building ...