// CODE SNIPPET
505.4.2 Apartment and Sleeping Rooms
JUMP TO FULL CODE CHAPTER
Except as otherwise provided in FC505.4.1, and except in buildings protected throughout by a sprinkler system, in a Group R-1 or R-2 building or occupancy with more than eight dwelling units on a floor, each dwelling unit shall be identified on the door jamb on the public corridor side of the door by an approved fire emergency marking, not more than 12 inches (305 mm) from the bottom of the door, indicating the dwelling unit number and/or letter.
Related Code Sections
3.3.10 Definitions, Dwelling Unit (For Sprinkler System Installations)
, sanitary, and sleeping facilities that include, but are not limited to, hotel rooms, dormitory rooms, apartments, condominiums, sleeping rooms ...
Standard for the Installation of Sprinkler Systems 2016 of New York City > 3 Definitions > 3.3 General Definitions > 3.3.10 Dwelling Unit (For Sprinkler System Installations)
310.2 Use and Occupancy Classification, Definitions
The following terms are defined in Chapter 2: APARTMENT. APARTMENT, STUDENT. BOARDER (ROOMER, LODGER). CONGREGATE LIVING UNIT ...
NYC Building Code 2022 > 3 Use and Occupancy Classification > 310 Residential Group R > 310.2 Definitions
Appendix A Selected Rules of the Department of Buildings [PDF] (page 117)
, apartments and rooms in which they are to be placed, including the number of rooms in the apartment and the occupancy of each room, whether sleeping ...
Appendix A Selected Rules of the Department of Buildings [PDF] (page 50)
the dwelling without passing through any sleeping room, bathroom or water-closet compartment. In apartments used for "single room occupancy" there shall ...
Appendix A Selected Rules of the Department of Buildings [PDF] (page 119)
piping supplying gas to the apartment. §40-37 Appliances in Sleeping Rooms. (a) Gas-fueled water heaters shall not be installed in a room occupied ...