// CODE SNIPPET
504.1 Antisiphon Devices
Related Code Sections
504.1 Water Heaters, Antisiphon Devices
An approved means, such as a cold water "dip" tube with a hole at the top or a vacuum relief valve installed in the cold water supply line above ...
5704.2.9.7.9 Flammable and Combustible Liquids, Antisiphon Devices
Approved antisiphon devices shall be installed in each external pipe connected to the protected above-ground tank where the pipe extends below ...
Fire Code 2018 of Kansas > 57 Flammable and Combustible Liquids > 5704 Storage > 5704.2 Tank Storage > 5704.2.9 Above-Ground Tanks > 5704.2.9.7 Additional Requirements for Protected Above-Ground Tanks > 5704.2.9.7.9 Antisiphon Devices
5706.2.5.1.1 Flammable and Combustible Liquids, Pumps and Fittings
to its hanger to prevent tampering. An effective antisiphoning device shall be included in the pump discharge unless a self-closing nozzle is provided ...
Fire Code 2018 of Kansas > 57 Flammable and Combustible Liquids > 5706 Special Operations > 5706.2 Storage and Dispensing of Flammable and Combustible Liquids on Farms and Construction Sites > 5706.2.5 Type of Tank > 5706.2.5.1 Tanks With Top Openings Only > 5706.2.5.1.1 Pumps and Fittings
1301.4 Fuel Oil Piping and Storage, Fuel Tanks, Piping and Valves
of the tank, an approved antisiphon valve or other siphon-breaking device shall be installed in lieu of the shutoff valve ...
Mechanical Code 2018 of Kansas > 13 Fuel Oil Piping and Storage > 1301 General > 1301.4 Fuel Tanks, Piping and Valves
5706.5.3.1.3 Flammable and Combustible Liquids, Antisiphon Valves
Antisiphon valves shall be provided where the system design would allow siphonage ...
Fire Code 2018 of Kansas > 57 Flammable and Combustible Liquids > 5706 Special Operations > 5706.5 Bulk Transfer and Process Transfer Operations > 5706.5.3 Process Transfer > 5706.5.3.1 Piping, Valves, Hoses and Fittings > 5706.5.3.1.3 Antisiphon Valves