// CODE SNIPPET
I 7.3 Anchors
JUMP TO FULL CODE CHAPTER
Anchors shall be
- used to restrict PEX tubing movement;
- made of materials that provide rigidity to the support system and utilize pipe clamps designed for plastic tubing capable of restraining the tubing; and
- installed in accordance with Figures 1 or 2, as applicable (i.e., anchor distances and size of arms and offsets).
Related Code Sections
(D) Equipment for General Use, Anchoring
Heating cables shall be positioned or secured in place under the floor covering, per the manufacturer's instructions ...
National Electrical Code 2017 of Nevada > 4 Equipment for General Use > 424 Fixed Electric Space-Heating Equipment > 424.45 Installation of Cables Under Floor Coverings > (D) Anchoring
I 7.3 Installation Standard for PEX Tubing Systems for Hot- And Cold-Water Distribution, Anchors
Anchors shall be used to restrict PEX tubing movement; made of materials that provide rigidity to the support system and utilize pipe clamps ...
2018 Uniform Plumbing Code of Nevada > I Installation Standard for PEX Tubing Systems for Hot- And Cold-Water Distribution > I 7.0 Hangers and Supports > I 7.3 Anchors
Chapter 17 Anchoring to Concrete
18.2.3 Earthquake-Resistant Structures, Anchoring to Concrete
Anchors resisting earthquake-induced forces in structures assigned to SDC C, D, E, or F shall be in accordance with 17.2.3 ...
Building Code Requirements for Structural Concrete of Nevada > 18 Earthquake-Resistant Structures > 18.2 General > 18.2.3 Anchoring to Concrete