// CODE SNIPPET
(3) Ampacity Relative to Service Conductors
Related Code Sections
(3) Wiring and Protection, Ampacity Relative to Service Conductors
The feeder conductor ampacity shall not be less than that of the service conductors where the feeder conductors carry the total load supplied ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 215 Feeders > 215.2 Minimum Rating and Size > (A) Feeders Not More Than 1000 Volts > (3) Ampacity Relative to Service Conductors
(B) Special Conditions, Conductor Ampacity
The ampacity of the feeder circuit conductors from the ESS(s) to the wiring system serving the loads to be serviced by the system shall not be less ...
National Electrical Code 2020 of Minnesota > 7 Special Conditions > 706 Energy Storage Systems > 706.30 Circuit Sizing and Current > (B) Conductor Ampacity
230.23 Wiring and Protection, Size and Ampacity
Conductors shall have sufficient ampacity to carry the current for the load as calculated in accordance with Article 220 and shall have adequate ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 230 Services > 230.23 Size and Ampacity
330.80 Wiring Methods and Materials, Ampacity
The ampacity of Type MC cable shall be determined in accordance with 310.14 or 311.60 for 14 AWG and larger conductors and in accordance with Table ...
National Electrical Code 2020 of Minnesota > 3 Wiring Methods and Materials > 330 Metal-Clad Cable: Type MC > 330.80 Ampacity
(2) Wiring and Protection, Ampacity
The neutral conductor shall be of sufficient ampacity for the load imposed on the conductor but not less than 33 1 / 3 percent of the ampacity ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 250 Grounding and Bonding > 250.184 Solidly Grounded Neutral Systems > (A) Neutral Conductor > (2) Ampacity