// CODE SNIPPET
608.5.1.1 Alternative Suppression Systems
JUMP TO FULL CODE CHAPTER
Battery systems that utilize water reactive materials shall be protected by an approved alternative automatic fireextinguishing system in accordance with Section 904. The system shall be listed for protecting the type, arrangement and quantities of storage batteries in the room. The fire code official shall be permitted to approve the alternate fire suppression system based on full-scale fire and fault condition testing conducted or witnessed and reported by an approved laboratory.
Related Code Sections
608.5.1.1 Building Services and Systems, Alternative Suppression Systems
official shall be permitted to approve the alternate fire suppression system based on full-scale fire and fault condition testing conducted or witnessed ...
California Fire Code 2016 > 6 Building Services and Systems > 608 Stationary Storage Battery Systems > 608.5 Suppression and Detection Systems > 608.5.1 Fire Suppression Systems > 608.5.1.1 Alternative Suppression Systems
126.96.36.199 Marine Systems,
Spaces shall be permitted to be protected with an alternative, approved fire suppression system where such areas are separated from the sprinklered ...
Standard for the Installation of Sprinkler Systems 2016 of California > 26 Marine Systems > 26.1 General > 26.1.5* Partial Installations > 188.8.131.52
184.108.40.206.3 Special Occupancy Requirements,
or a crack in a moderate- energy line can be isolated so as not to impair both the primary and the backup fire suppression systems unless otherwise ...
Standard for the Installation of Sprinkler Systems 2016 of California > 22 Special Occupancy Requirements > 22.27 Advanced Light Water Reactor Electric Generating Plants > 22.27.2 Installation Requirements > 220.127.116.11 Yard Mains, Hydrants, and Building Standpipes > 18.104.22.168.3
1206.5.5 Energy Systems, Fire Suppression Systems
Rooms and areas within buildings and walk-in units containing electrochemical ESS shall be protected by an automatic fire suppression system ...
California Fire Code 2019 > 12 Energy Systems > 1206 Electrical Energy Storage Systems (ESS) > 1206.5 Electrochemical ESS Protection > 1206.5.5 Fire Suppression Systems
(F) Special Conditions, Temporary Source of Power for Maintenance or Repair of the Alternate Source of Power
or structure is unoccupied and fire suppression systems are fully functional and do not require an alternate power source. Other temporary means can ...
California Electrical Code 2019 > 7 Special Conditions > 700 Emergency Systems > 700.3 Tests and Maintenance > (F) Temporary Source of Power for Maintenance or Repair of the Alternate Source of Power