// CODE SNIPPET
550.31 Allowable Demand Factors
JUMP TO FULL CODE CHAPTER
Park electrical wiring systems shall be calculated (at 120/240 volts) on the larger of the following:
- 16,000 volt-amperes for each mobile home lot
- The load calculated in accordance with 550.18 for the largest typical mobile home that each lot will accept
|Number of Mobile Homes||Demand Factor (%)|
|61 and over||22|
Related Code Sections
550.31 Special Occupancies, Allowable Demand Factors
to calculate the feeder or service load in accordance with Table 550.31. No demand factor shall be allowed for any other load, except as provided in this Code ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 550 Mobile Homes, Manufactured Homes, and Mobile Home Parks > 550.31 Allowable Demand Factors
(B) Special Equipment, Demand Factors
is installed. The demand factors set forth in Table 626.11(B) shall be the minimum allowable demand factors that shall be permitted for calculating load ...
National Electrical Code 2020 of Minnesota > 6 Special Equipment > 626 Electrified Truck Parking Spaces > 626.11 Feeder and Service Load Calculations > (B) Demand Factors
(A) Special Occupancies, Basis of Calculations
sites. The demand factors set forth in Table 551.73(A) shall be the minimum allowable demand factors that shall be permitted in calculating load ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 551 Recreational Vehicles and Recreational Vehicle Parks > 551.73 Calculated Load > (A) Basis of Calculations
430.26 Equipment for General Use, Feeder Demand Factor
and duties. Informational Note: Demand factors determined in the design of new facilities can often be validated against actual historical experience ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 430 Motors, Motor Circuits, and Controllers > 430.26 Feeder Demand Factor
620.14 Special Equipment, Feeder Demand Factor
Demand Factors for Elevators Number of Elevators on a Single Feeder Demand Factor* 1 1.00 2 0.95 3 0.90 4 ...
National Electrical Code 2020 of Minnesota > 6 Special Equipment > 620 Elevators, Dumbwaiters, Escalators, Moving Walks, Platform Lifts, and Stairway Chairlifts > 620.14 Feeder Demand Factor