// CODE SNIPPET
3109.3 All Swimming Pools
JUMP TO FULL CODE CHAPTER
Public and private swimming pools shall comply with the requirements for safety and accessibility as provided in this section.
Where the suction inlet system, such as an automatic cleaning system, is a vacuum cleaner system which has a single suction inlet, or multiple suction inlets which can be isolated by valves, each suction inlet shall protect against user entrapment by an approved antivortex cover, a 12-inch by 12-inch (305 mm by 305 mm) or larger grate, or other approved means. In addition, all swimming pools and spas shall be equipped with an alternative backup system which shall provide vacuum relief should grate covers be missing. Alternative vacuum relief devices shall include one of the following:
- Approved vacuum release system.
- Approved vent piping.
- Other approved devices or means.
No overhead electrical conductors shall be installed within 15 feet (4572 mm) of any swimming pool. All metal fences, enclosures, or railings that might become electrically charged as a result of contact with broken overhead conductors or from any other cause near, or adjacent to, a swimming pool shall be grounded in accordance with the provisions of lightning protection in the New York City Electrical Code.