// CODE SNIPPET
[F] 904.3.4 Alarms and Warning Signs
JUMP TO FULL CODE CHAPTER
Where alarms are required to indicate the operation of automatic fire-extinguishing systems, distinctive audible and visible alarms and warning signs shall be provided to warn of pending agent discharge. Where exposure to automatic-extinguishing agents poses a hazard to persons and a delay is required to ensure the evacuation of occupants before agent discharge, a separate warning signal shall be provided to alert occupants once agent discharge has begun. Audible signals shall be in accordance with Section 907.5.2.
Related Code Sections
904.3.4 Fire Protection and Life Safety Systems, Alarms and Warning Signs
Where alarms are required to indicate the operation of automatic fire-extinguishing systems, distinctive audible and visible alarms and warning signs ...
Building Code 2018 of Illinois > 9 Fire Protection and Life Safety Systems > 904 Alternative Automatic Fire-Extinguishing Systems > 904.3 Installation > 904.3.4 Alarms and Warning Signs
422.214.171.124 Special Detailed Requirements Based on Occupancy and Use, Leakage Alarm
on every entry door to the tank storage room indicating the potential hazard of the interior room environment, or the sign shall state: WARNING, WHEN ALARM ...
Building Code 2018 of Illinois > 4 Special Detailed Requirements Based on Occupancy and Use > 415 Groups H-1, H-2, H-3, H-4 and H-5 > 415.9 Group H-2 > 415.9.1 Flammable and Combustible Liquids > 4126.96.36.199 Leakage Alarm
(C) General, Warning Signs
Entrances to rooms and other guarded locations that contain exposed live parts shall be marked with conspicuous warning signs forbidding unqualified ...
National Electrical Code 2017 of Illinois > 1 General > 110 Requirements for Electrical Installations > 110.27 Guarding of Live Parts > (C) Warning Signs
300.45 Wiring Methods and Materials, Warning Signs
Warning signs shall be conspicuously posted at points of access to conductors in all conduit systems and cable systems. The warning sign(s) shall ...
National Electrical Code 2017 of Illinois > 3 Wiring Methods and Materials > 300 General Requirements for Wiring Methods and Materials > 300.45 Warning Signs