1224.14.3 Airborne Infection Isolation Rooms
Single rooms shall be provided for the isolation of patients with airborne communicable disease at a ratio of one room for each 35 licensed beds, and for each major fraction thereof. At least one airborne infection isolation room shall be provided. Airborne infection isolation rooms shall be labeled with the words "Airborne Infection Room" on or adjacent to the anteroom side of the door between the isolation room and the anteroom.
A separate anteroom shall be provided between the airborne infection isolation room and the corridor, which shall constitute the primary entrance to the airborne infection isolation room. This anteroom shall have a handwashing fixture, work counter at least 3 feet (914 mm) long, cabinets and space to gown and to store clean and soiled materials. There shall be a view window from the anteroom to the isolation room and means to allow for airflow from the anteroom into the airborne infection isolation room. Doors shall be aligned to allow large equipment to be wheeled into the airborne infection isolation room unless a secondary door complying with Section 1184.108.40.206 is provided. One anteroom may serve no more than two airborne infection isolation rooms.
When a secondary entry is provided, the secondary doors shall be provided with locking devices which are readily operable from the room side and which are readily operable by the facility staff on the other side. When key locks are used on isolation rooms, keys shall be located at the nurses' station in a prominent readily accessible location.