// CODE SNIPPET
AF103.2.5 Air-Conditioning Systems
Related Code Sections
AF103.2.5 Passive Radon Gas Controls, Air-Conditioning Systems
Entry points, joints or other openings into air-conditioning systems in enclosed crawl spaces shall be sealed. Exception: Systems ...
2015 Michigan Residential Code > F Passive Radon Gas Controls > AF103 Passive Radon-Resistant System Requirements > AF103.2 Entry Routes > AF103.2.5 Air-Conditioning Systems
1107.6 Refrigeration, Joints and Refrigerant-Containing Parts in Air Ducts
Joints and all refrigerant-containing parts of a refrigerating system located in an air duct of an air-conditioning system carrying conditioned air ...
2015 Michigan Mechanical Code > 11 Refrigeration > 1107 Refrigerant Piping > 1107.6 Joints and Refrigerant-Containing Parts in Air Ducts
1700.2 Process Piping, Process Piping
Piping which is not part of a refrigeration system or part of a system designed to provide air conditioning. Process piping includes pipes which ...
907.2.13.1.2 Fire Protection Systems, Duct Smoke Detection
of an air-conditioning system. In Group R-1 and R-2 occupancies, a smoke detector is allowed to be used in each return air riser carrying not more than 5,000 ...
2015 Michigan Building Code > 9 Fire Protection Systems > 907 Fire Alarm and Detection Systems > 907.2 Where Required-New Buildings and Structures > 907.2.13 High-Rise Buildings > 907.2.13.1 Automatic Smoke Detection > 907.2.13.1.2 Duct Smoke Detection